With the development of society and economy, more and more families have begun to use domestic ro membrane to purify water. In fact, domestic ro membrane are artificial semi-permeable membranes that simulate microbial semi-permeable membranes and are the key prefabricated components of membrane separation technology. . The basic principle of membrane separation technology is that under the action of higher than the osmotic concentration of the solvent, other components cannot be separated through the semi-permeable membrane.
1. Pollution type of domestic ro membrane.
In the entire equipment application process, in addition to all the normal performance degradation, the performance of the equipment and membrella ro membrane will be more severely degraded due to pollution. General pollutants include organic chemical dirt, organic compounds, colloids, microorganisms, etc. Distinguish the pollution types from the aspects of source water body, pollution level, operation records, equipment performance changes, etc.:
Microbial contamination: When microbial contamination occurs, the throughput of membrella ro membrane and the number of pathogens in the concentrated water are of high quality, which is closely related to the careless maintenance, disinfection and sterilization in normal times.
Colloidal pollution: When colloidal pollution occurs, there are generally two characteristics. The first is to solve the problem of rapid blockage of small and medium-sized filter devices, especially the rapid increase of working pressure. The second is that the SDI value exceeds 2.5.
2. The cleaning method of domestic ro membrane.
a. Use a pump to pump clean, non-dispersed chlorine pure water from the cleaning tank into the pressure vessel and discharge it for several minutes.
b. Use pure water to configure the cleaning solution in the cleaning tank.
c. Circulate the cleaning fluid in the pressure vessel for 1 hour or a predetermined time in advance. For an 8-inch or 8.5-inch pressure vessel, the flow rate is 35-40 gallons/min, and for a 6-inch pressure vessel, the flow rate is 15~ 20 gallons/min, for a 4-inch pressure vessel, the flow rate is 9~10 gallons/min
d. After cleaning, drain the cleaning box and carry out cleaning, and then fill the cleaning box with clean product water for the next step of cleaning.
e. Use a pump to pump clean, non-dispersed chlorine pure water from the cleaning tank into the pressure vessel and discharge it for several minutes.
f. After cleaning the reverse osmosis system, operate the reverse osmosis system with the pure water discharge valve open until the water is cleaned and there is no foam or cleaning agent. It usually takes 15 to 30 minutes.
The ro system membrane has a small diameter, which can effectively remove dissolved acid salts, colloidal solutions, microorganisms, organic compounds, etc. in the water.